The medical gas console outlet shall be Ohio Medical Healthcair® Series. The outlets shall be UL Listed, NFPA compliant, cleaned for
medical gas service and be pressure tested. Each outlet shall have less than 3 psi (21kPa) pressure drop through the outlet @ 120 l/
min. and 50 psig (345 kPa) inlet pressure. For outlets providing positive pressure gas, the outlet shall be equipped with a primary and
secondary check valve, the secondary check valve shall be rated for 200 psi (1,379 kPa) allowing the primary check valve to be removed for service without isolating the entire zone.
The console outlets shall have a gas specific back body which can accommodate up to a 3/4 “(19 mm) plate. Each back body shall be equipped with a 6-1/2” (165 mm) length type “K” copper pipe stub which is brazed to the outlet body. The outside diameter of the copper pipe stub shall be 1/2” (12.7 mm). The inlet pipe can be swiveled 360 degrees for ease of installation.
Outlet bodies shall be gas specific by means of a gas specific indexing pin arrangement. The indexing pins shall be arranged in such
a way as to connect the latch-valve assembly only with the specific matching gas back body, preventing interchangeability of gas
The latch-valve assembly which, by means of color coding and wording shall identify the specific medical gas service provided by the outlet and shall accept gas specific adapters.
Ohio Medical Corporation is an ISO 13485 registered facility.